Improved to change the lightning rod from the original model System 3000 to replace it with the model LPI Stormaster 60 ESE, the grounding cable is a COAXIAL CABLE 80/50mm.
The top must coordinate with the bottom as much as possible.
With the head lowered, it's time to remove the original head. and put a new head Stomaster ESE 60
Set up the pole and attach it to make it strong.
Verify that the ground system below is in perfect condition with lightning power.
Test to measure the resistance of the ground system. It reads 0.85 ohms, which is a very good value. Finish work and go home